Japanese Earthquake Update (14 March 00:30 UTC) - Clarified
Based on information provided by Japanese authorities, the IAEA can confirm the following information about the status of Units 1, 2 and 3 at Fukushima Daiichi nuclear power plant.
Unit 1 is being powered by mobile power generators on site, and work continues to restore power to the plant. There is currently no power via off-site power supply or backup diesel generators being provided to the plant. Seawater and boron are being injected into the reactor vessel to cool the reactor. Due to the explosion on 12 March, the outer shell of the containment building has been lost.
Unit 2 is being powered by mobile power generators on site, and work continues to restore power to the plant. There is currently neither off-site power supply nor backup diesel generators providing power to the plant. The reactor core is being cooled through reactor core isolation cooling, a procedure used to remove heat from the core. The current reactor water level is lower than normal but remains steady. The outer shell of the containment building is intact at Unit 2.
Unit 3 does not have off-site power supply nor backup diesel generators providing power to the plant. As the high pressure injection system and other attempts to cool the reactor core have failed, injection of water and boron into the reactor vessel has commenced. Water levels inside the reactor vessel increased steadily for a certain amount of time but readings indicating the water level inside the pressure vessel are no longer showing an increase. The reason behind this is unknown at this point in time. To relieve pressure, venting of the containment started on 13 March at 9:20AM local Japan time. Planning is underway to reduce the concentration of hydrogen inside the containment building. The containment building is intact at Unit 3.
The IAEA is seeking information about the status of spent fuel at the Daiichi plant.